hoping someone can help me here. so ive installed 4 dimmers fine but oddly enough im having a hard time with a switch. i guess i have a 3 way switch? I have lights that are controlled by 2 switches. The wiring is shown below, i have 1 of each type. i have power to the device but other than the lights flicking on for a half a second i cannot get them to connect and right now I'm chalking it up to the 3 way issue. should I try to install the switch on the other end of the 3 way?
the connection to me seems easy b/c off the bat the neutrail and ground wires are spoken for. that would only leave live and load and ive tried each with both wire options and still nothing.